27’-4” diameter of primarily unlined tunnel beneath Lake Michigan
Peak daily capacity of 2.2 billion gallons of cooling water
- The Elm Road generating station (ERGS) needed a cleaner, more efficient system of cooling technology.
- The ERGS Cooling Water Intake System was constructed by Kenny/Shea JV.
- It consists of a lake-water intake tunnel excavated in rock and is 9,226-foot long; 27’-4” in diameter.
- Approximately 2,000 feet of the tunnel is lined to a finished diameter of 25 feet.
- The new water intake tunnel can supply a total of 2.2 billion gallons per day of cooling water to the existing Oak Creek and new Elm Road power plants.
- This design-build contract combined drill-and-blast and tunnel-boring machine (TBM) operations using main beam gripper TBM and rock-support selection based on the geotechnical-baseline reporting of rock mass classifications.
- The dike wall structure was approximately 250-feet long and contained nine gates to provide cooling water under emergency tunnel bypass conditions.
- Difficult marine construction involved dredging, cofferdam construction, and underwater work while maintaining a cooling water supply to the existing Oak Creek Power Plant (OCPP).
- A sunken caisson construction was used for on-shore mining and OCPP shafts.
- After completing tunnel mining, the TBM machine was disassembled underneath Lake Michigan and carried in pieces back to beginning of the tunnel for removal.
How we can help you
If you have a problem that needs to be solved, please get in touch.
Mount Royal Tunnel double arch replacement
Montreal, Quebec, Canada
Minneapolis weathers the storm with a new parallel tunnel
Minneapolis, MN, USA
Kemano Second Tunnel (T2) Project
British Columbia, Canada
Burnhamthorpe Water Project
Regional Connector Transit Corridor
North-West PATH Tunnel
Eglinton Crosstown Light Rail Transit
Toronto, Ontario, Canada